Window Air Conditioner Troubleshooting, A Step By Step Guide
With this window air conditioner troubleshooting guide, you get the technical
knowledge to diagnose and repair your unit. The typical service call would cost over $100. With this
guide, you can do it yourself and save that money.
**NOTE** ONLY YOU CAN ASSESS YOUR ABILITY TO PERFORM THIS TASK. THIS IS A GUIDE AND
CANNOT PROVIDE ALL OF THE DETAILS FOR EVERY SITUATION.
You should begin your window air conditioner troubleshooting by ensuring that
maintenance has been performed on the unit.
Then, your window air conditioner troubleshooting should start with checking
the different modes of operation to see which components operate. Turn the unit fan to on and the cool
and heat modes off. If the fan does not operate, check the power supply to the unit. Check to see if the
breaker or fuse for the unit is tripped. If the breaker/fuse is tripped, check to make sure that it is
the proper size circuit for the unit you have. On some units, there is a current interruptor on the
power cord to the unit. Check to see if it is tripped by pushing the reset button.
If the circuit is the proper size, then you can go ahead and reset the
breaker/fuse. If it trips again, then you require further troubleshooting. Shut the power off and check
all of the wiring in the unit to make sure that none of the connections is loose or damaged.
If the fan does not operate but the fuse/breaker is not tripped, you should
check the run
capacitors for the fan and compressor. If the capacitors are good but the fan motor does not
operate, you can check the fan switch and the fan motor. Ensure that the fan blades spin freely.
If the fan motor operates but the compressor does not start, you should feel
the compressor with your hand. If it is very hot, then you should allow it to cool. Then, you can take
resistance measurements to make sure the compressor motor is good.
Then, you should attempt to start the unit in the cooling mode. As you do so,
listen for a clicking sound which is an indication that it is attempting to start. If the compressor
starts but does not cool properly, the unit may be low on refrigerant.